Good Pilot, call for heat, valve opens, good flame*, no blower, valve closes.
Fan switched to ON Blower works.
My first thought is a limit switch, can they be Jumpered to see which one?
Any other thoughts appreciated.
Questions about repairs and parts for Coleman furnaces, air conditioners and heat pumps for manufactured homes. Click here for Coleman parts.
2 posts • Page 1 of 1