about 2 weeks ago our heat went out and I replaced the sequencer. It has been fine until last night this horrible smell came thru the vents and upon checking the new sequencer was really hot, I turned off the unit and tripped the braker.
we are going to put another sequencer in tomorrow but could it be anything else?
We have an electric coleman evcon
Thanks in advance
Questions about repairs and parts for Coleman furnaces, air conditioners and heat pumps for manufactured homes. Click here for Coleman parts.
2 posts • Page 1 of 1