We no longer have a relationship with a parts store. Following a link on this page will take you to Amazon.com to search for it. It may or may not be available depending on availability. This is the best we can do at this time and we hope it helps.
105144000R Time Delay Relay$25.06
Time delay relay used in some Miller direct ignition burners. 24V coil. Turns on in 30-60 seconds (H30-60) and off in 1-30 seconds (C1-30). Replaces 105144000.
Relay – time delay. H30-90. H24V. 15SHI. Replaces 104381000, 104381 & 309572. Time delay relay used in some Miller standing pilot burners. Turns on in 1-30 seconds (H1-30) and off in 30-60 seconds (C30-60).
Nordyne 01-0157 SPDT 24V coil relay$12.00
Nordyne replacement fan motor relay. New style, perfect fit!Terminals 1 & 3 are for 24v input. Terminals 5 and 6 are normally closed (NC) and terminals 2 and 4 are normally open (NO). When 24V is applied to terminals 1 and 3, terminals 5 & 6 will open while terminals 2 and 4 will close.Replaces 01-0157, 620537, 620689, 621871 & 621873. ÿAlso known as Packard PR380.Technician Note: ÿDon’t get too caught-up with the terminology of SPDT (single pole double throw), SPST (single pole single throw), DPST (double pole single throw) and DPDT (double pole double throw). ÿRarely is the proper terminology assigned correctly to a relay. ÿSort of depends upon who’s interpreting it when the relay is labeled. ÿIf any concerns, give us a call. ÿ
Double pole single throw blower and fan relay. 24V coil. With the power off, terminals 5 & 6 will be closed and terminals 2 and 4 will be open. With 24V to terminals 1 & 3, terminals 5 & 6 will be open and terminals 2 and 4 will be closed. Be sure to remove wires from terminals 2,4,5 & 6 before testing. Also known as # 9400-13Q152. Replaces 620537, 6205370, 620689, 6206890, 621867, 6218670, 621873, 628337, 6283370, 660190, 104786000 & 105521000.
621869R SPDT Relay$11.95
Single pole double throw relay. 24V coil. With the power off, terminals 5 & 6 will be closed and terminals 2 and 6 will be open. With 24V to terminals 1 & 3, terminals 5 & 6 will be open and terminals 2 and 6 will be closed. Be sure to remove wires from terminals 2,4 & 6 before testing. Also known as 9400-14Q152. Replaces 621097, 621869 & 103963002.