Questions about repairs and parts for Nordyne furnaces, air conditioners and heat pumps for manufactured homes including Intertherm, Mac and Miller brands. Click here
for Nordyne parts.
Moderators: ponch37300, Mark, flcruising, Greg
My furnace quit working after a power outtage and I have tried and re-tried tripping and re-setting all the breakers a couple of times. I have shut all the buttons on the furnace off and back on as well.
My question is this: Is there a reset button on it somewhere? I have been unable to find one.
It is an Intertherm MAC 2460 No. A 878269 60,000 BTU/hr. 240 volts. I suspect it is original to the mobile (which would make it about 30 yrs.old) but I don't know for sure.
Any and all help greatly appreciated! It's cold where I live. I don't know much about repairs so I'm a beginner here.
First establish that it didn't blow out the transformer. Make sure you have 24VAC low voltage coming from LOAD/SECONDARY side of transformer.
Also check for any blown fuses in circuit. Then jumper one limit switch at a time to see if any of those are open.
Some people are Humbly Grateful, while some are Grumbly Hateful.................... Which one are you ?
- Posts: 6413
- Joined: Wed Feb 28, 2007 12:07 am
- Location: Tennessee
Return to Nordyne Service & Repair
Who is online
Users browsing this forum: No registered users and 1 guest