Questions about repairs and parts for Nordyne furnaces, air conditioners and heat pumps for manufactured homes including Intertherm, Mac and Miller brands. Click here
for Nordyne parts.
Moderators: ponch37300, Mark, flcruising, Greg
Our Intertherm runs continuosly and will not shut-off. The fan and heater blow hot-air all day, until we turn off the breaker. Turning the thermostat all the way down does not have any effect.
Any ideas or suggestions?
Pending a short or something somewhere, probably the most common problem is a stuck sequencer. The sequencer part number for your furnace is 901075, which can be seen and ordered here: http://www.mobilehomerepair.com/NordyneElec.html
You can't fail if you don't try!
Follow me on Twitter.
- Site Admin
- Posts: 735
- Joined: Sat Feb 17, 2007 4:23 pm
- Location: Aberdeen, SD
I have now ordered the sequencer; hopefully that will do the trick.
I am thinking about updating the thermostat (to one of the programmable ones) - what style should I be looking for, or is it even possible to install a programmable thermostat?
Just be sure it is for your units, heat and a/c types with same number of wires as minimum.
It will have to be battery operated or you will need to run a common wire from transformer to t-stat C connection.
I would get a Honeywell or White Rodgers and would buy from HVAC supply if possible. Better t-stats and knowledgeable help to get correct t-stat.
Take care and best wishes,
Some people are Humbly Grateful, while some are Grumbly Hateful.................... Which one are you ?
- Posts: 6413
- Joined: Wed Feb 28, 2007 12:07 am
- Location: Tennessee
Return to Nordyne Service & Repair
Who is online
Users browsing this forum: Google [Bot], Yahoo [Bot] and 1 guest