Questions about repairs and parts for Coleman furnaces, air conditioners and heat pumps for manufactured homes. Click here
for Coleman parts.
Moderators: ponch37300, Mark, flcruising, Greg
i have a coleman evcon model#dgat070bde.i tried the heater out today and the unit will not come on.the air conditioner works fine and blows cold,but no heat.the little green light on the box flashes green 3 times.the stickers says"centrifugal switch failes to close".whats going on with this thing.thanks in advance for any help
- Posts: 1
- Joined: Sun Oct 04, 2009 4:24 pm
That can be due to combustion motor being faulty, the centrifugal switch inside the motor being faulty or the comb. motor air pipe being damaged/clogged.
Most often it is the motor or switch and since the switch cannot be bought separately from the motor, either way requires a new combustion motor.
Let me know if interested in ordering info. Would need an hvac tech to test everything to see which one is at fault for sure.
Some people are Humbly Grateful, while some are Grumbly Hateful.................... Which one are you ?
- Posts: 6413
- Joined: Wed Feb 28, 2007 12:07 am
- Location: Tennessee
Return to Coleman Service & Repair
Who is online
Users browsing this forum: Bing [Bot], Google [Bot], Google Adsense [Bot], Yahoo [Bot] and 2 guests