Questions about repairs and parts for Coleman furnaces, air conditioners and heat pumps for manufactured homes. Click here
for Coleman parts.
Moderators: ponch37300, Mark, flcruising, Greg
What are upper and lower limit switches supposed to be? I think mine is too high
Upper = 7680-3791= Open @ 140*/Close @ 120*
Lower = 7660-3591 = Open @ 150*/Close @ 130*
Fan- Limit = 7700-3281 = Open @ 120*/Close @ 90*
Thanks for inquiring,
Some people are Humbly Grateful, while some are Grumbly Hateful.................... Which one are you ?
- Posts: 6413
- Joined: Wed Feb 28, 2007 12:07 am
- Location: Tennessee
Return to Coleman Service & Repair
Who is online
Users browsing this forum: MSNbot Media and 5 guests