Fan does not come on when heat starts. Most of the time, now, the heater comes on (at thermostat - heat -), coils get hot, no fan. to the point I am selecting fan on thermostat to disperse heat from coils. From what I've learned.
1. Thermostat starts heater and low fan - (Mine: coils heat - NO fan)
Am I right to suspect the Sequencer or what would be 1st step?
Questions about repairs and parts for Coleman furnaces, air conditioners and heat pumps for manufactured homes. Click here for Coleman parts.
2 posts • Page 1 of 1